KD-type sodium hypochlorite generator is an equipment that can produce the disinfectant by electrolyzing
the brine of diluting industrial salt or seawater. Sodium hypochlorite is strong oxidant and disinfector, which can be used to disinfecting the water .It has good bactericidal effect, safe and convenient, with a shorter contacting time.
This equipment is widely used in the sewage treatment works in the hospital, the circulating water treatment works at swimming pools and natatorium, intermediate water treatment works, feeding chlorine for industrial circulating water, and the treatment of industrial waste water with cyanogens. Besides, it can be used to disinfect drinking water, vegetables, fruit, wasting room, ward, blanch the paper pulp and hemp, and disinfect drinking water and living place for the fowl, etc.
A: Its manufactured according to the GB12176-90 standard, all the targets have reached the A level of national standard.
B: Adopting PLC program control and sequencing batch principle of operation, preparing 10g/l sodium hypochlorite disinfectant batch after batch till the finished products is filled with the box.
The automatic control steps are as follow:
1) Check the liquid level of finished product case
2) If it is not full, switch on the salt water pump and fill the electrolysis bath with salt water.
3) Then, switch off the pump, and start a constant current and voltage electrolysis for 60-90 minutes.
4) When time's over, switch on the power valve of the downing liquid, the finished disinfectant flow into the case.
5) Then, the positive and negative poles would be rotate automatic.
6) Repeat all the steps for 1-5 till the finished product case is full, then, the equipment would stop automatically.
C: It is generated by the non-membrane electrolysis of the common salt water, the request of the turbidity is not strict.
D: High activity of titanium anode, long useful life, and electrolysis by batch, save salt and the electricity
E: full-automation control, it just need feeding salt by artificial for 3 to 10 days.
F: Pipeline and valve, pipe fitting all adopt the U-PVC engineering plastics, with good corrosion resistance and tightness.
G: The whole set of equipment is with high full- automatic and convenient to use.
H: The fitting of equipment is with high quality of standardization and good interchangeability.
I: In the electrolysis of each batch, the positive and negative poles would be rotate automatic, so it has no scale formation of the electrode, and no request to the solidity of the brine. It can be widely used for the long electrode life and high use ratio of the electrolysis bath.
2: technical function
current efficiency in electric tank:75%
direct current power consumption: 4kw.h/kg available chlorine
salt consumption: 4kg/kg available chlorine
production of available chlorine: 10g/h -3000 g/h
anode Durability forecasting: 30000h
3: type selection of equipment
chemical dosing parameter of each water treatment types
A: hospital sewage treatment
It can treat the hospital sewage which the scale of the hospital is 50-1000 sheets of bedspaces, the fees of treatment is 0.11RMB per one ton water.
Main technical parameters:
chlorine feeding: the amount of polyclinic sewage feed according to the 25-30g/t.The contacting time is longer than 1 hour. The standard of lazaretto is 35-40g/t, the contacting time is longer than 1.5 hour.
B: Disinfection of tap water and drinking water
The Scale is 10-5000t/h (ton per hour).The type selection of equipment is according to the amount and flow rate of the clarified water pump, the treatment fee is 0.0085RMB per one ton water.
Add chlorine: 1.5g/t(tap water and drinking water)
After 30 minutes contacting time, the chlorinity mustn't be lower than 0.3mg/L.The chlorinity in the dead end of the distribution network should be higher than 0.05mg/L.
C: Water treatment of the swimming pools
Our company can offer the complete set of circulating water treatment equipment for swimming pools and natatorium with the scale of 500-5000 ton water.(including sterilizing epuipment, filter plant, batch feeding equipment, water circulating pump, hair filter, etc). The treatment fee is 0.025rmb per one ton water.
chlorine feeding: the feeding amount according to 5g/t (the rest chlorinity in the pool should maintain in 0.3-0.7mg/l)
D: water treatment for drinking water and food of poultry
It can be adopted for different kinds and scales of plants
(disinfection for drinking water, enviroment), food products factory (disinfection for food utensil, surrounding, drinking water)
Feeding amount and type selection of equipment:
1.drinking water 1.5g/T
2.swimming pool 5g/T
3. reclaimed water, 8g/T
4.hospital sewage and domestic sewage 25g/T
4: operating cost
one kilogram available chlorine directly fees:6.00rmb/kg
beside: current drain 5kw X 0.5rmb=2.50rmb
salt consumption 4kg X 0.8rmb/kw=3.20rmb
water consumption 0.2T X 1.5rmb/T=0.30rmb
Contact Name: Ms.cherise Yan
Company Name: Chongqing Chenming Water Treatment Equipment Co
Street Address: Apt.2-23-1,
Xinchengxinzuo, Erlang, Jiulongpo
District, Chongqing, China
27 September 2011
10 watertreat Import Export Business Leads
Chlorine Dioxide Generator, Sodium Hypochlorite Generator, Ozone Generator
Chat with watertreat
Verify: Safe Import Export Tips