JS Aluminum Type MC Cable is constructed with Type XHHW-2 conductors rated 90℃ wet or dry, and
a bare equipment grounding conductor. The Conductors are AA-8000 series Aluminum Alloy compact stranded. A binder tape is wrapped over the conductors with interlocked aluminum tape applied over the assembly. Aluminum interlocking armor is applied over the assembly. Refer to color chart for conductor color sequence.
APPLICATIONS suitable for use as follows:
Branch, feeder and service power distribution under high ambient temperatures in commercial, industrial, institutional, and multi-residential buildings.
Power, lighting, control, and signal circuits.
Fished or embedded in plaster.
Concealed or exposed installations.
Environmental air-handling spaces per NEC©300.22(c).
Places of Assembly per NEC®518.4 and theaters per NEC®520.5.
As aerial cable on a messenger.
installation in cable tray and approved raceways.
Under raised floors for information technology equipment conductors and cables per NEC®645.5(D) & 645 (D)(2)
•UL Classified 1, 2, and 3 Hour Through-Penetration Fire-stop Systems:W-J-3037, W-L-3110, W-L-3113, W-L-3117, W-L-3120, W-L-3121, W-L-3160, C-AJ-3115, C-AJ-3140, C-AJ-3142, C-AJ-3145, C-AJ-3173, C-AJ-3202, C-AJ-4065, C-AJ-4066, F-C-3038.
•Cable reverse wound on reel for ease of pulling and installation. When pulling from coils, pull from inside to ensure ease of installation.
•Anti-short bushings are not required for use with MC Cable per the NEC® and UL.
Contact Name: Jayson
Company Name: Js Int'l Group Ltd
Street Address: 2-16 Fa Yuen St Mong
Member name: jsighk
Member Since: 05 July 2017
Total Leads: 7 jsighk Import Export Business Leads
Business focus: Biometric Attendance System, Access Control, Aluminum Alloy Cable, Cosmetic
Verify: Safe Import Export Tips
Product Category: Electric lead wires or cables