1. Due to improper selection of plate heat exchanger plates, cracks or perforations are caused
by plate corrosion.
2. The operating conditions do not meet the design requirements.
3. The residual stress after cold stamping of the plate and the clamping size during assembly are too small to cause stress corrosion.
4. There is a slight leakage in the plate leakage groove, which causes the harmful substances in the medium (such as C1) to concentrate and corrode the plates, forming a string of liquid.
1. Replace the cracked or pierced plates, and use the light transmission method to find the cracks on the plate.
2. Adjust the operating parameters to meet the design conditions.
3. The clamping size of the plate heat exchanger during maintenance and assembly should meet the requirements, not as small as possible.
4. Reasonable matching of plate materials.
Wuxi Jiusheng Heat Exchanger Co., Ltd. is one of the largest and earliest suppliers of aluminum plate-fin heat exchangers in China. We have 15 years of production experience and are experts in this field. Among them, the Automobile Intercooler we produce has product quality assurance. In addition to this, JS has developed and produced a wide range of aluminium plate-fin heat exchangers for many industry sectors. If you are interested in our products, please contact us.
Contact Name: Harrison
Company Name: Wuxi Jiusheng Heat Exchanger Co., Ltd.
Tel: +86 18206171482
Street Address: Room 2313 No.8
Tianshan Road, High-tech Zone,
Wuxi City, Jiangsu Province 214000
Member name: JiushengHeatExchanger
Member Since: 13 October 2021
Total Leads: 22 JiushengHeatExchanger Import Export Business Leads
Business focus: Automobile Intercooler, Air Compressor, Construction Machinery Hydraulic Oil Cooler, Agricultural Machine Oil Cooler
Verify: Safe Import Export Tips